Lawrence Webster Forrest
Tel: +44 (0)20 8668 8663 Fax: +44 (0)20 8668 8583
Lawrence Webster Forrest
Tel: +44 (0)20 8668 8663 Fax: +44 (0)20 8668 8583
An important part of a building's infrastructure is the ducting network that runs throughout the premises, it is often invisible, but is a key element to the environmental operations in a building. Ducting may carry fresh air to improve the environmental ambience for the occupants in the building, or may serve a dirtier role in helping to remove smells, dust or toxic gases from a room or piece of equipment. It may also form part of the vital systems to protect occupants from the effects of smoke, or help prevent fire spread. Whatever its role, most ductwork must travel extended distances through a building to reach its destination – usually the open air or treatment plant.
What’s so important about ductwork?
Not much notice is taken of the ductwork in a building – indeed it and its associated dampers are often neglected and forgotten. We can never underestimate the importance of these systems, both in keeping us comfortable, or as far as risking our lives or the integrity of the building to which it is installed.
Buildings are designed with fire resistant enclosures, known as compartments, to contain any fire within one area. Due to its possible routes through a building, ductwork is a key element that can, if not suitably protected, weaken the passive fire protection built into a building through the construction of fire walls and floors / ceilings. Without adequate fire resistance, along with the other services installed such as plumbing, electrical wiring or communication cabling, this can lead to rapid uncontrolled spread of smoke and fire through an entire building, often without the occupants being aware for some time.
Why make ductwork fire resistant?
Fire resistant ductwork and dampers can prevent fire spread from the room of origin, thus protecting occupants, and the fabric of the building.
While specially made fire resistant ductwork can be acquired, there are also different methods of protecting ductwork. It can be enclosed within a fire resisting material, commonly plasterboard or other substance designed specifically for this purpose. Dampers can be fitted within the compartment wall to seal the building structure in the event of a fire.
In the same way that fire doors are provided within compartment walls, dampers are also provided within compartment walls and floors where ducting passes. These allow free access throughout the ducting system normally, but will shut down and prevent the passage of smoke and flames between compartments in the event of a fire. Dampers can be linked to the fire alarm and close when this is triggered, or thermal links may activate when exposed to high temperatures . These are typically set to activate at temperatures of 72°C ± 4°C.
As with fire doors, ductwork and damper fire resistance must match the fire rating of the compartment through which they pass or are installed in.
There may be many reasons why fire resisting ductwork and dampers are installed, for example:
1. To be used for smoke extract in the case of a fire in fire engineered solutions.
This may be the case in basements, car parks or means of escape, to increase the available safe egress time for occupants by helping prevent the build up of toxic gases and heat. The ducting is responsible for removing smoke from an area, which can reach high temperatures very quickly. The system, including any fans, must also be able to withstand these high temperatures long enough that all occupants can safely evacuate.
Where smoke extract is required in basement areas, these areas must also be provided with sprinklers. The ductwork in this case must be able to prevent water ingress as well as high temperatures, and also the possibility of thermal shock from sprinkler systems activating.
2. Kitchen extract systems (non domestic).
These systems are a particular risk, especially if the required maintenance and cleaning regimes are not adhered to. The build up of grease and fat within the ducting, coupled with high temperatures, can self ignite and cause a fire in the ducting itself. It is important that this fire does not break out of the ducting into adjacent rooms or service risers, and that radiant heat is minimised to prevent ignition of a second fire outside the duct.
It must be noted that dampers must not be installed to kitchen extract systems, so further emphasis on the fire resistance of the ducting is made.
3. The ductwork passes through a means of escape.
Where the ductwork must pass through a means of escape, then it must be capable of protecting that escape route from a fire in the adjacent rooms to which it is linked, much like the fire doors to which we are accustomed.
What makes ductwork fire resistant?
Ductwork must pass three key tests before it can conform to British Standards:
Tests are performed on the ducting as a whole, including joints and hangers, so you can be assured that the whole system will perform as required in the event of a fire.
In order to achieve adequate fire resistance, ducting can be treated in various ways. The ducting can be coated, sprayed, enclosed or wrapped in a wide range of proprietary materials available from a large number of manufacturers. As with maintenance of the ductwork itself, the protection supplied must also be maintained and protected from damage when works are carried out.
As can be seen from this bulletin, fire resistant ductwork and dampers can be key to preventing unforeseen fire spread throughout your building. It is therefore imperative that if any works are being undertaken to ductwork within your property that you clearly understand any fire rating or resistance that maybe necessary to that ductwork.
This bulletin has been written by Karissa Thomas DipHE Fire Safety.
In LWF's Fire Engineering blog series for Architects and others involved in building design, we have been looking at firefighting. In part 17, we began to look at how firefighting is undertaken by the Fire Service and their objectives and modes of operation when arriving at a fire. In part 19, tactical firefighting is discussed.While the general objectives of tactical firefighting were given in the last blog, there are various methods used by firefighters...
In LWFs blog series for healthcare professionals, the aim is to give information on best practice of fire safety in hospitals and other healthcare premises. In part 51 of this series, we were looking at the potential for fire spread from one area of a building to another through external surfaces, before moving on to begin to look at the necessary arrangements for car parks. In part 52, we continue on that theme by considering...
In LWFs blog series for those who work in Facilities Management or who have an interest in or responsibility for fire safety we have been looking at fire safety engineering. In part 8, we looked at how ASET (Available Safe Egress Time) is calculated and how this should always be more than the RSET (Required Safe Egress Time). While ASET involves a series of calculations relating to fire growth and the building itself, RSET, also...
In LWF’s fire engineering blog series for Architects and others in the business of building design, we have been looking at firefighting. In part 16, we discussed first-aid firefighting by the occupancy and the use of hose reels to do so. In part 17, we will begin to look at firefighting from the point of view of the Fire Services.The particular objectives of the Fire Service in a given situation will be decided upon...
In LWF’s blog series for healthcare professionals, the aim is to give information on best practice of fire safety in hospitals and other healthcare premises. In part 50 of this series, we discussed the potential for external fire spread including calculating unprotected areas and consideration of the surfaces of external walls and roofs. In part 51, we continue looking at external fire spread, starting with junctions of different elements.At the junction of wall and...
The Wohl Neuroscience Institute - Fire Safety, Strategy & Engineering
Key Facts: Client: King’s Clinical Neuroscience Institute Project Manager: MACE Ltd Designers: Devereux Architects/Allies and Morrison Approximate Size: 7,400m2 Description of the Project:...
Fire - The External Risk
When we consider fire safety, our focus is normally from within, what can we do to prevent the occurrence of fire and how we can limit its damage.Â Whilst this is the correct stance to take, we m...
Evacuation Modelling - Factor in Human Behaviour
Evacuation of buildings can be analyzed in different ways. Approved Document B (ADB) which provides guidance on meeting the requirements of the England and Wales Building Regulations with regard to fi...