Lawrence Webster Forrest
Tel: +44 (0)20 8668 8663 Fax: +44 (0)20 8668 8583
Lawrence Webster Forrest
Tel: +44 (0)20 8668 8663 Fax: +44 (0)20 8668 8583
Unwanted Fire Signals is the formal term given to what has been universally referred to as 'false alarms'. Unwanted fire signals is considered to encompass the issue and this will become apparent as we expand on this issue.
The majority of building users do not appreciate the local impact of unwanted fire signals or the wider impact. It is considered that there are two fundamental problems arising from unwanted signals, namely:
· Desensitisation of fire alarms within buildings
· Diverting essential resources away from emergency services
It is important that we expand on these issues. With regards to desensitising fire alarms, this is very apparent in some buildings whereby common faults on the fire alarm mean the evacuation signal is frequently given, consequently occupants, on hearing the fire alarm immediately assume the alarm to be false. Whilst on the majority of occasions, this may well be the case, the behaviour of occupants, in terms of escape time is likely to have a negative effect, with extreme cases leading to occupants opting not to evacuate at all. It is clear that this behaviour is unacceptable in terms of fire safety, but it is also understood that this is a learned response which needs addressing.
With regards to diverting emergency services, this is fairly self explanatory if the local Fire Service attend fire alarm activations within the building, which in itself will be dependant on a number of factors, including your geographic location (which Fire Authority you fall under), the building occupancy as well as the type of fire alarm you have and whether it is monitored, building operators should always strive to ensure that emergency services are called in emergencies only, in the current climate, where increasing pressure is placed on resources, this is paramount.
There are a number of secondary (non fire safety issues) that will be of significance to building occupiers also and these will often be the key drivers for change, particularly where there is a commercial impact. The main issue is business disruption. This often increases with the size of the building, due to the number of occupants that require evacuating, although other factors, such as the building occupancy / use will have a significant impact, for example, evacuation of a theatre or cinema would be extremely disruptive and would be likely to have commercial implications.
On the basis of the above, it is clear to see the importance of ensuring a fire alarm activates in a 'real' condition only. We must now consider how to ensure that is the case.
Ideally, the fire alarm system has been appropriately designed and installed with appropriate maintenance in place. This must be the first objective. In existing buildings, it is likely that building management will be able to have an influence over the maintenance aspect only, this is however an important function, lack on system maintenance is a common reported fault.
Reporting. This is a simple identification technique to identify problem areas. For example, if false alarms frequently occur on the 3rd floor between 9am and 9:30am, this will give a strong indication of what activity is causing the unwanted signal. Once this has been identified, action can be taken, this could range from prohibiting the activity to changing the local detector heads (following specialist advice).
Delayed evacuation signal - in some instances, this will be appropriate. This method is commonly used within numerous buildings and when adopted appropriately is advantageous. Effectively, the fire alarm system can be reconfigured so that multiple sensors are required to activate prior to the fire alarm sounding. It must however be noted that this effectively reduces the sensitivity of the fire alarm and requires careful and specialist consideration, an enhanced level of fire detection and building management may also be required. It must also be noted that activation of manual call points would normally initiate an immediate evacuation signal. Also, this system allows a pre-determined delay period, allowing building management time to investigate the initial activation, if no further information is provided, i.e. 'the all clear' is not given within the time, the alarm will sound.
A very simple but effective tool is a fire risk assessment. The assessment should take account of the fire risks presents set against the fire detection present. The risk assessment should also review any unwanted fire signals and be able to ascertain the reason for false activation. It is likely that the risk assessment will recommend simple, but effective measures, such as replacement of faulty sensor heads / alteration of detector type, for example, changing a smoke detector to a heat detector.
It is clear from the discussion above that the reduction of false alarms is fundamental. It is also noted that there are some very simple but effective measures that can be implemented to ensure that life safety is achieved, with no unnecessary disruption to building users and without placing a burden on the emergency services.
If you would like to know more – or would like to arrange an appointment with one of our senior fire safety advisers – simply call Peter Gyere on 020 8668 8663.
In LWF’s fire engineering blog series for Architects and other professionals involved in building design, we have been looking at firefighting and, most recently, the provisions that should be made for the Fire Service to attend and put out a fire. In part 23, we looked at the requirements and recommendations relating to the provision of fire hydrants and we continue from that point in part 24.The original standards for the installation of water...
In LWFs blog series for healthcare professionals, the aim is to give information on best practice of fire safety in hospitals and other healthcare premises. In part 57 of this series, LWF looked at what access and facilities must be provided for the Fire Service attending a fire at a healthcare venue. In part 58, we will continue from that point by looking at the number and location of fire-fighting shafts required in those healthcare...
In LWF’s blog series for those professionals who work in facilities management or who have an interest in or responsibility for fire safety, we have been looking at property protection and the role of the insurer. In part 4, some of the history that led to property insurance from fire was given and in part 5, we will continue looking at how different the early insurers could be from what we know today.While the...
In LWFs fire engineering blog series for Architects and others involved in building design, we have been looking at the subject of firefighting. In part 22, we gave information on some of the regulations and guidance documents which deal with the issue of provision of fire hydrants. In part 23, we continue from that point by looking at who should provide them and where they should be placed in relation to the building.
In LWFs blog series for healthcare professionals, the aim is to give information on best practice of fire safety in hospitals and other healthcare premises. In part 56 of this series, LWF spent time looking at the access required by Fire and Rescue Service vehicles to healthcare buildings not fitted with fire mains. In part 57, LWF will continue looking at those measures which should be taken to ensure the Fire Service has access to...
The Wohl Neuroscience Institute - Fire Safety, Strategy & Engineering
Key Facts: Client: King’s Clinical Neuroscience Institute Project Manager: MACE Ltd Designers: Devereux Architects/Allies and Morrison Approximate Size: 7,400m2 Description of the Project:...
Fire - The External Risk
When we consider fire safety, our focus is normally from within, what can we do to prevent the occurrence of fire and how we can limit its damage.Â Whilst this is the correct stance to take, we m...
Evacuation Modelling - Factor in Human Behaviour
Evacuation of buildings can be analyzed in different ways. Approved Document B (ADB) which provides guidance on meeting the requirements of the England and Wales Building Regulations with regard to fi...